2. Press the Start push-button to crank the engine; the engine will start and run off-line. When the ‘Generator Available’ LED is on (after a delay to allow the oil pressure to rise) the generator can be manually switched on-line by pressing the manual mode close generator push-button. Only carry out this operation in emergency situations where the generator has failed to start during a utility mains failure.
3. Pressing the Stop push-button will stop the generator immediately.
4. Pressing the Auto push-button will start the auto shutdown sequence.
After manual operation, when the engine has stopped, ensure that the generator is returned to automatic operation by operating the Auto push-button, and that the heater switch is in the ‘ON’ position.
How to Operate a Deep Sea Controller – Basic User information
The cookie settings on this website are set to "allow cookies" to give you the best browsing experience possible. If you continue to use this website without changing your cookie settings or you click "Accept" below then you are consenting to this.