Generators – How to manually switch ABB Motorised Switch
Most of the time your automatic changeover panel will happily automatically change from mains to generator and back on its own. What happens though on that one occasion where there is a problem with the motorised switch and it doesn’t change over? What can you do to get your power to your building on whilst waiting for an engineer? Well its actually very straight forward. If it is an ABB motorised switch, follow the instructions below.
To manually switch the ABB motorised switch, firstly place the switch into Manual mode by pushing the lever switch on the front of the switch. Once you have done this, connect the key onto the front of the switch until it clicks into place. Switch as desired. To place back into automatic mode, remove the key, by pressing the button below it. Flick the lever switch back to Auto.
Search – Knowledge Base