Phase shift happens what there is more than one power feed coming into a building. Each transformer supply needs to have the same phase rotation and the identical phase location. (zero)
If there is only one supply, then there is no issue.
On the other hand, if you have two supplies, then these need to be checked at the point of installation & need to be set up to ensure NO phase shift between them.
When installing N+1 UPS systems being feed by TWO Gird supplies via TWO transformers it is essential that the building management have already ensured that the phase rotation is the same for both in coming supplies and that there is no phase shift between the supplies
What if you find out there is phase shift?
Then the power harmonics will be out and the wave form disputed, causng down stream power issues to equipment within the Data Centre
Example photo – These wave forms Should be identical – NOT like this image:
The wave form for the two supplies should look like this.
Image after works.
Find where the phase shift has happened. The transformer? Ring Main? LV panels? Locate it. Prove it. And then repair the issue, as soon as possible.
This may require major infrastructure upgrade works but this is a necessity.
Call Power Continuity on 0845 055 8455 and we can fix your phase shift issues!
The cookie settings on this website are set to "allow cookies" to give you the best browsing experience possible. If you continue to use this website without changing your cookie settings or you click "Accept" below then you are consenting to this.