What are Uninterruptible Power Supplies (UPS) – Design Functionality?
The design of the Uninterruptible Power Supply is determined by the required function also by what the level of critical cover expected to protect the load.
At the bottom end of the scale are ‘desk tops’, the offline UPS system, generally below 1kVA. As its name suggests, it provides an unregulated filtered supply to the load, while at the same time maintaining the state of charge of the battery by means of a separate charger.
When the utility mains fails or goes out of tolerance the inverter turns on and is connected to the load via a relay. There is a short break while this operation takes place and the duration of this break is called the transfer time.
The Offline UPS system is not suitable where there are large variations in the local utility mains supply, as the load will be directly affected. To overcome this problem a Line Interactive UPS system can be used. The technology operates in a very similar way to the Offline UPS systems. Whereas the inverter does not provide supply to the load unless a utility mains failure or brownout has occurred.
The Line Interactive UPS system uses an active voltage regulator (AVR) to control the voltage seen by the load during normal operation; this method ensures that the load has a constant voltage applied to it. Additionally, these Uninterruptible Power Supplies are more suitable for small office environment loads and restricted to a maximum of 10kVA.
Double Conversion UPS system’s
Traditionally, for larger load requirements, the Double Conversion UPS system is prefered. Basically it consists of a rectifier, battery, inverter and static switch. This is generally termed as a True On-line UPS. The term ‘True On-Line’ is used, as this type of UPS will protect your mission critical equipment. Even to the point that removing its power source and then re-instigating the power, will have not effect on your equipment.
How does it work?
The True On-Line Uninterruptible power supply works by having a rectifier, which converts the utility mains AC supply to DC. This has the dual function of providing a DC supply for the inverter. Also a supply to recharge the battery. Therefore, in the event of the utility mains failing, or going out of tolerance, (due to voltage or frequency causing the rectifier to switch off), the battery will seamlessly continue. Providing the DC supply for the inverter.
The inverter then converts the DC supply back to an AC supply. It is voltage and frequency controlled to supply the load. The utility mains supply load is therefore, completely protected from surges, spikes or sags.
The double conversion Uninterruptible Power Supply has the added advantage of having a static switch. This is an electronic changeover power switch, which selects the supply required for the load. The supply can be either the unprotected utility mains supply or the fully protected inverter supply. This feature can be very useful in the event of an overload that is beyond the rating of the inverter. The load will automatically transfer without loss to the utility mains supply. Transferring back to the protected inverter supply when the fault is removed.
Search – Knowledge Base